Edisi yang lain - Lihat semua
absorbed actual amount analysis ascertain atmospheric atomizing boiler burner California calorimeter capacity carbon cent chapter chimney coal Company compute connected contains correction damper determined draft economizer efficiency Electric energy engineering entering evaporation factor feed fire flame flow flue force formula fuel oil furnace gage gases give given gravity heat Hence hour illustration important inches increased indicates installed known less load loss means measured mechanical method moisture necessary obtained operation oxygen pass pipe placed plant plate possible pound practice pressure production pump quantity reading regulating represent Rule sample saturated scale seen showing shown specific standard steam storage superheat superheated supply surface tables taken tank temperature tubes units valve volume weight
Halaman 15 - Change of motion is proportional to the impressed force and takes place in the direction of the straight line in which the force acts.
Halaman 412 - Earthwork embankments shall be firmly and compactly built of good earth from which stones, vegetable matter, etc., have been removed, and shall have a flat section at...
Halaman 413 - All joints shall be riveted and caulked, brazed, welded or made tight by some equally satisfactory process. Tanks shall be tight and sufficiently strong to bear without injury the most severe strains to which they may be subjected in practice. Shells of tanks shall be properly reinforced where connections are made, and all connections made through the top of tank above the liquid level.1 3.
Halaman 415 - Tanks located underground shall have top of tank at least three feet below the surface of the ground, and below the level of the lowest pipe in the building to be supplied. Tanks may be permitted underneath a building if buried at least three feet below the lowest floor. Tanks shall be set on a firm foundation and surrounded with soft earth or sand, well tamped into place or encased in concrete.
Halaman 227 - C.) to the weight of an equal volume of distilled water at the same temperature, both weights being corrected for the buoyancy of air.
Halaman 130 - The name and location of the refinery, if the oil has been refined at all. "13. The fuel oil is to be delivered fob cars or vessel, according to the manner of shipment, at such places, at such times, and in such quantities as may be required, during the fiscal year ending.
Halaman 411 - Rules and Requirements of the National Board of Fire Underwriters for the Installation of Electric Wiring, as Recommended by the Underwriters' National Electrical Association.
Halaman 130 - Allen proposes the following specifications for fuel oil to be purchased by the government : (1) In determining the award of a contract, consideration will be given to the quality of the fuel offered by the bidders, as well as the price, and should it appear to be to the best interest of the Government to award a contract at a higher price than that named in the lowest bid or bids received, the contract will be so awarded. (2) Fuel oil should be either a natural homogeneous oil or a homogeneous residue...
Halaman 420 - Control valves shall be provided with stuffing box of liberal size, containing a removable cupped gland designed to compress the packing against the valve stem and arranged so as to facilitate removal. Valves shall be designed to close against the supply, and to prevent withdrawal of stem by continued operation of the handwheel. Packing affected by the oil or by heat shall not be used.